390, 5250 session, AIX, AMD, Architecture/Design, Automated, Blade servers, Cabling, CICS, configuration, CPU usage, Data Center, Data center cooling, Data center design, Data Center in 2010, Data Center management, Data center operations, Data center planning, Data Center power management, Data Centers, Dell, Dell PowerEdge, Energy efficiency, Enterprise architecture, Hewlett-Packard, IBM, IBM Mainframe, Intel, Internet of Things, IPL, iSeries data center, IT architecture, IT Infrastructure, JCL, Mac, Mainframe, Novell, Operating system platforms, Power management, Server consolidation, Servers, Solaris, Sun, Sun Microsystems, Technology, Upgrades / implementations, UPS, Vendor support, Vendors, z/OS VIEW ALL TAGS
When you decided to implement hot-aisle/cold-aisle containment in your data center, did you consult any best practices guides? What made you decide that a hot-aisle/cold-aisle solution was right for your setup?
In a hot aisle/cold aisle floor design, best practices are not to mix the hot air with the cold air. I am using blanking panels, floor grommets, everything that I've learned over the years in managing data centers to get the optimal cooling from my CRAC units. One question I have relateing to...