390, 5250 session, AIX, AMD, Architecture/Design, Automated, Blade servers, Cabling, CICS, configuration, Data Center, Data center cooling, Data center design, Data Center in 2010, Data center infrastructure, Data Center management, Data center operations, Data center planning, Data Center power management, Data Centers, Dell, Dell PowerEdge, Dell PowerEdge 2800, Dell servers, Energy efficiency, Enterprise architecture, Hewlett-Packard, IBM, IBM Mainframe, Intel, IPL, iSeries data center, IT architecture, IT Infrastructure, JCL, Mac, Mainframe, Novell, Operating system platforms, Power management, Server consolidation, Servers, Solaris, Sun, Sun Microsystems, Upgrades / implementations, UPS, Vendor support, Vendors, z/OS VIEW ALL TAGS
We just bought a RockAutonmaiton circuit breaker(http://samplecode.rockwellautomation.com/idc/groups/literature/documents/td/1489-td001_-en-p.pdf). The question is how to install the circle breaker? Thanks.
I have been asked to purchase a supply of CAT-5e network cables for use in our data center racks. I am having trouble estimating how many of each length we will need. Is there a rule of thumb for making this type of estimate, say, for a fully populated and properly configured standard rack?
Need to consolidate 4 DC in US and 2 in Canada into a single DC. Please sugggest a checklist from n/w and server side which can help getting all answers