390, 5250 session, AIX, AMD, Architecture/Design, Automated, Blade servers, Cabling, CICS, configuration, CPU usage, Data Center, Data center cooling, Data center design, Data Center in 2010, Data Center management, Data center operations, Data center planning, Data Center power management, Data Centers, Dell, Dell PowerEdge, Energy efficiency, Enterprise architecture, Hewlett-Packard, IBM, IBM Mainframe, Intel, Internet of Things, IPL, iSeries data center, IT architecture, IT Infrastructure, JCL, Mac, Mainframe, Novell, Operating system platforms, Power management, Server consolidation, Servers, Solaris, Sun, Sun Microsystems, Technology, Upgrades / implementations, UPS, Vendor support, Vendors, z/OS VIEW ALL TAGS
I have just started working in data center and have noticed a stulz VFS-240-DAR-D with only one hot gas bypass it does have two compressors. Could any one plz tell me why this would be why.
A SearchDataCenter.com reader wrote in with this question: 200 kVA is the load in our 25+ year-old 6,800 sq. ft. "data center" as measured from the UPS. · What should the theoretical cooling requirement (in tons of cooling) be using downdraft CRACs? · By what factor or amount might that cooling...